The heating pipe network system with such dynamic characteristics as nonlinearity and large time lag may cause hydraulic disorder. To solve this problem, this paper proposes a unit control-based hydraulic equilibrium control strategy, which constructs an equilibrium regulation system for heating pipe networks by optimising the inlet device of each unit and using a novel control theory. By developing a cascade control system to control the return water temperature and the pressure difference between supply and return water of the branches at each unit of the pipe network, we were able to stabilise the pressure and control the temperature. Then, we used the averaging control theory to set the parameters of regulation systems between each unit. The research results indicate that, compared to the traditional single-loop negative-feedback return water temperature control system, the cascade averaging controller has a better control effect than the single-loop PID controller. This is because it has a smaller overshoot and can cope with system interference factors quickly. Therefore, the temperature of return water between each unit can be coordinated and fluctuation is within a smaller range. This effectively eliminates the influence of static and dynamic hydraulic disorder on entire system stability.

#### Keywords

- heating pipe network
- hydraulic disorder
- cascade control system
- averaging control

In an urban heating pipe network, intelligent regulation and equilibrium control are the core of the entire system operation [1], and the control condition will greatly affect the power and heat consumption of the entire heating system [2]. Currently, central heating still faces the problems that (1) in case of lack of effective regulation at the terminals of a heating system, hydraulic disorder may result in uneven indoor temperatures of different users; and (2) in order to maintain the heat supply of users with lower indoor temperature, the heat output from the heat source is increased, which leads to excessive heating and overall overheating loss [3–5]. Therefore, the pipe network flow should be controlled in a reasonable range so that it can satisfy heat consumers’ needs and help to save energy and reduce consumption of the entire heating system.

To improve hydraulic disorder in the heating pipe network, a various types of research have been carried out in the industry, and a lot of hydraulic equilibrium regulation methods have been raised. Common regulation methods include a proportional regulation method, compensational regulation method, return water temperature method etc. [6]. Both proportional regulation method and compensational regulation method require the regulating staffs to perform a related heating theoretical calculation before regulation operation. Comparatively, the return water temperature method is simpler. It only takes return water temperature as a regulating target. However, the traditional return water temperature method has the weaknesses of regulating time delay and indoor temperature not fully represented by return water temperature. This paper puts forward an automatic levelling scheme that can remedy the demerits of the traditional return water temperature method.

The secondary heating network system has strong thermal inertia and a larger time constant during the heat transfer process [7, 8]; so, traditional temperature regulation measures cannot provide precise control over the controlled object. Meanwhile, the heating system often adopts a branch-shaped pipe network [9, 10], which leads to hydraulic disorder in the system; see Figure 1 for the system diagram. Though a large number of studies and demonstrations on the hydraulic disorder of pipe networks have been conducted in the industry, problems exist to varying extents and these can be attributed to the practicality of operating effect, such as high cost and poor regulating effect [11]. In contrast with from previous strategies that a system needs to be regulated repeatedly by professional staffs according to their experience, this system proposes a unit controlbased hydraulic equilibrium control strategy. It is a unit control-based equilibrium regulation system for heating pipe networks, which optimises the device at the unit inlet and applies the structure of novel control theories.

This system decomposes the controlled objects with larger delay, takes the pressure difference and return water temperature required by heat consumers of each unit as control parameters to design a cascade averaging control system and transmits the heating network data remotely by IoT technology and equipment to the remote monitoring centre of the heating company. The managing staffs of the company could regulate automatically according to various data of heating system, stabilise the pressures of each branch and meanwhile compare the measured return water temperature with the set value of return water temperature issued by the remote monitoring centre. Then, they can adjust the electric control valve installed at the unit entrance of each building and change the flow of the pipeline. When the re-measured return water temperature and real working pressure difference of all units are basically the same, it can be said that the hydraulic and thermodynamic equilibrium of the secondary network system is achieved.

At the same time, the indoor temperature data collectors are installed in the home as part of heat consumers in the building; this is done to monitor the indoor temperature of typical consumers in real time, which provides an indoor temperature reference for equilibrium regulation of secondary network and can ensure the heating quality [12, 13].

The equilibrium regulation system collects such signals as supply and return water pressure difference and returns water temperature at heat inlet of all units in the community through PLC controller of all buildings. Then, it communicates with the remote control centre, controls the designated electric regulating valve through a novel algorithm and adjusts valve opening to affect the pipeline flow, enabling the return water temperature to reach a stable value. The structure of the entire heating network equilibrium system is divided into three layers: a bottom layer, a network layer and a remote control layer. The bottom layer is the on-site control part, in which PLC control cabinets are installed in each building to collect the return water temperature and supply and return water pressure data of each unit. Moreover, a new control algorithm is run in PLC’s CPU (through PLC’s new control strategy) to adjust corresponding electric regulating valves and to transmit collected data into the system’s network layer. In the network layer, various parameters of the system in the PLC host are transmitted via an optical fibre conversion device in the control cabinet to the exchanger of the heat exchange station in the community. Then, through connecting to WAN via a router, by way of port mapping, the summarised heating network data is interacted to the host computer, to realise remote transmission. After that, in the remote control layer, the data is displayed in the Supervisory Control And Data Acquisition (SCADA) system, and a selfdesigned operation interface makes it possible to monitor the bottom layer data in real time and to manually set and automatically adjust valve opening. The overall structure of the system is shown in Figure 2.

In a heating pipe network system, the different distance between different heat consumers and the heat source centre leads to the discrepancy of the residual pressure heads in the pipelines of different heat consumers. Different residual pressure heads make the flow into each heat consumer not conform to the designed value, and thus, hydraulic disorder generates [14]; when the secondary pipeline is well heat-preserved, that is, if the supply water temperature is the same, the temperature of return water in the pipeline can accurately reflect the heat disorder of the pipe network [15, 16].

The heating pipe network has strong thermal inertia and a larger time constant during heat transfer, and so traditional temperature regulation means could not provide precise control over the controlled object. In order to satisfy overall heat consumers’ demand for indoor temperature, a unit-specific regulation scheme is designed and reasonable temperature and pressure observation points are set at the heat inlet of each unit in the community. In this way, the controlled objects with larger delay are decomposed, and a disturbance variable with frequent and large-range changes is found from the return water temperature of originally controlled objects. That is, the temperature _{H}_{L}_{L}_{1} on the network will affect Δ_{L}_{H}_{L}_{L}

The control system principle diagram is shown in Figure 4. Let us suppose that pipeline clogging or household valve lockup occurs at the heat consumer side. If such an influential condition will act on a minor object, then it can be categorised as disturbance _{1} in the figure. This results in the decrease of pressure required by the heat consumer side and the increase of residual pressure difference in this unit branch. Thus, when other influential factors remain unchanged, the flow and temperature provided by the heat exchange station will also be kept the same. Immediately, at the measuring points of this project, the working pressure difference Δ_{L}_{L}_{L}_{R}_{L}

If we assume that the supply and return water pressure difference at the heat inlet of the original unit is under the effect of regulated flow _{02}(

Then,

According to the existing experiments, if the output characteristic of the electric regulation valve is set as _{v}_{m2}(

Eq. (1) is converted to

In a normal-operation condition of heating network, _{c2}_{v}_{m2}_{02} >> 1; so, when the regulation process of the minor loop causes amplification coefficient _{02} or _{v}_{L}_{H}_{H}_{H}_{L}_{L}

When the influential conditions act on the primary object, for example, the supply water temperature at the heat exchange station of a community fluctuates, or in-station valve disturbance causes flow fluctuation, as shown as _{2} in the figure. The in-station valve fluctuation may lead to the rise of supply water temperature in minor network and the unit working pressure difference Δ_{L}_{H}_{H}_{H}_{L}_{L}_{H}_{L}_{L}_{L}

The unit control-based hydraulic equilibrium regulation system is composed of a PLC controller, electric regulating valve, temperature sensor, pressure sensor, optical fibre converter and so on. The system structure is designed briefly, with clear control equipment, to ensure the regulation performance of valves. Therefore, the controller adopts SIEMENS S7-200 SMART type. The pressure and temperature sensors are connected with the PLC controller by shield cables to transmit signals, while the PLC controller supports open user communication protocol, which guarantees signal transmission in the whole process. This system takes return water temperature and supply and return water pressure difference as a basis of hydraulic equilibrium regulation, designs reasonable temperature and pressure measuring points in the heating network, installs temperature and pressure transmitter and measures return water temperature and supply and return water pressure difference in different unit pipelines. The PLC controllers allocated in buildings upload the measured return water temperature and supply and return water pressure difference to the remote control centre. Then the remote control centre will summarise return water temperature and supply and return water pressure difference in the unit pipeline of different buildings as well as outdoor temperature change to figure out the appropriate set value of return water temperature, and deliver it to the PLC controller. Later, each controller adjusts the electric regulating valve of each unit entrance by running a built-in control algorithm, ultimately enabling the return water temperature of each unit to reach an equilibrium value. Take a PLC controller designed in Building #1 as an example; see its design drawing in Figure 5.

According to the real monitored point number of hydraulic equilibrium regulation system based on unit control, in order to ensure that PLC terminal number accounts for 10–20% margin of total point number, the S7-200 SMART PLC’s CPU module is selected as SR30, the on-off input/output is 18 points/12 points and input/output form is DC 24 V input/AC 220 V relay output. On account of this, the system needs multi-path analogue input and output points, and so the analogue module needs to be extended. Take a building with two units as an example and extend two analogue modules EM AE08 of eight-module input selected in the input combination and one analogue module EM AQ04 of four-module output. The I/O point address assignment of this PLC CPU and the extended module are shown in Table 1.

I/O point address assignment.

Input | Output | ||
---|---|---|---|

I0.0 | System On | Q0.0 | Automatic operation indicator |

I0.1 | System Off | Q0.1 | Comprehensive alarm indicator |

I0.2 | Manu/Auto switchover | Q0.2 | Out-of-control valve in unit #1 higher zone |

I0.3 | Emergency cut-off | Q0.3 | Out-of-control valve in unit #1 lower zone |

AIW16 | Return water temperature in unit #1 higher zone | Q0.4 | Out-of-control valve in unit #2 higher zone |

AIW18 | Return water temperature in unit #1 lower zone | Q0.5 | Out-of-control valve in unit #2 lower zone |

AIW20 | Return water temperature in unit #2 higher zone | Q0.6 | Return water temperature alarm in unit #1 |

AIW22 | Return water temperature in unit #2 lower zone | Q0.7 | Return water temperature alarm in unit #2 |

AIW24 | Supply water pressure in unit #1 higher zone | Q1.0 | Supply and return pressure difference alarm in unit #1 |

AIW26 | Return water pressure in unit #1 higher zone | Q1.1 | Supply and return pressure difference alarm in unit #2 |

AIW28 | Supply water pressure in unit #1 lower zone | AQW48 | #1 Higher valve opening instruction |

AIW30 | Return water pressure in unit #1 lower zone | AQW50 | #1 Lower valve opening instruction |

AIW32 | Supply water pressure in unit #2 higher zone | AQW52 | #2 Higher valve opening instruction |

AIW34 | Return water pressure in unit #2 higher zone | AQW54 | #2 Lower valve opening instruction |

AIW36 | Supply water pressure in unit #2 lower zone | ||

AIW38 | Return water pressure in unit #2 lower zone | ||

AIW40 | Valve feedback in unit #1 higher zone | ||

AIW42 | Valve feedback in unit #1 lower zone | ||

AIW44 | Valve feedback in unit #2 higher zone | ||

AIW46 | Valve feedback in unit #2 lower zone |

In the unit control-based heating network equilibrium regulation system, the return water temperature of each unit is controlled by a cascade loop; this allows us to establish the relationship between the unit building’s heat load and the corresponding branch flow. Meanwhile, the heating system adopts a branch-shaped pipe network, with branches interconnected with each other. However, when the cascade system of one branch is disturbed by _{1} and _{2}, the regulating valve of this branch will adjust the flow, which will affect the fluctuation of other branches or even the entire pipe network. Frequent operation of regulating valve makes the flow of the branches to mutually interfere, and the equilibrium state of the water system in the pipe network changes with it, followed by the change of systemic hydraulic working condition. These cause systemic vibration and increases operating energy consumption. Regarding the compact regulation process between each unit branch, in traditional schemes, the valves are regulated repeatedly for many rounds according to human experience, resulting in excessively long systemic regulating time and higher professional requirements for regulating staffs. Therefore, this system solves the problem from the design of unit cascade control system scheme, and integrates with the idea of averaging control, so that the control effect can be moderate and the controller parameters caused by large output error range of control system in system regulation process can be optimised [18]. Under the disturbance of _{1} and _{2}, the return water temperature of the near-end unit branch has a small fluctuation in the allowable range. At the same time, the return water temperature of the far-end unit branch changes slowly in balance. By dynamically optimising the opening of electric regulating valves in each branch of the network system, the return water temperature parameters of each unit branch coordinate with each other to satisfy systemic dynamic hydraulic equilibrium. See the control program design of controllers in Figure 6 and the overall regulation procedure in Figure 7.

Application research was conducted in Dihao Community, Shijiazhuang city, and was carried out in accordance with standardised engineering practices. This community was built early in 2018, including nine high-rise residential buildings, with a total construction area of 118,435 m^{2} and a heating supply area of 43,188.62 m^{2}. The tail-end network path has an unreasonable route due to on-site construction conditions and unit load estimation deviation, and hydraulic disorder is obvious in near-end and tail-end heat consumers; owing to these reasons, it is necessary to improve the system. See detailed community information in Table 2.

Statistics of building condition in the community.

SN | Building No. | Unit qty. | Floor qty. | Construction area (m^{2}) |
Heating supply area (m^{2}) |
---|---|---|---|---|---|

1 | #1 | 3 | 18 | 23086.5 | 7632.46 |

2 | #2 | 2 | 18 | 9781 | 2337.86 |

3 | #3 | 2 | 18 | 15309.36 | 5181.87 |

4 | #4 | 2 | 18 | 16465.4 | 4188.8 |

5 | #5 | 2 | 12 | 10113.6 | 4194.52 |

6 | #6 | 2 | 18 | 16465.4 | 7502.58 |

7 | #7 | 2 | 18 | 9558.21 | 4501.11 |

8 | #8 | 2 | 11 | 9279.6 | 4254.63 |

9 | #9 | 2 | 16 | 8431.84 | 3394.79 |

The community adopts central heating. Municipal high-temperature hot water will exchange heat with the minor network after being conveyed to the heat exchange station in the community, and then low-temperature hot water will be conveyed into each building. Indoor heating adopts floor radiation, and the courtyard pipe network is laid by lifting at the top of the garage. See network laying in Figure 8.

After electrical engineering network-route design, system hardware installation, controller programming and system communication test, the summarised heat network data is interacted to the operation environment of the host computer to realise remote transmission and to display in the SCADA system in the remote control layer. By self-designing an operation interface, it is possible to monitor the bottom layer data, manually set and automatically adjust valve opening in real time. Then, the averaging cascade controller and PID parameters are optimised and debugged; finally, the levelling control system is ready to accept input, after which it can be operated stably in the long run. This effectively improves the control quality of the network system on temperature and pressure difference parameters. See SCADA system’s human-machine exchange interface in Figure 9.

After the heating system was completed in this community, the heating season had come, but the levelling system had not been installed yet. After water injection, multiple households of Unit 1 and one household of Unit 3 at the tail end of Building 1 complained about supercool indoor temperature. As the levelling system was not installed yet, the thermal power company performed a preliminary debugging, such as manually regulating valves, but showing poor effect. Afterwards, when the levelling system was completed, the heating system of the community was examined and debugged. The pre-debugging system data of that day is shown in Table 3. On December 27, it was sunny and the outdoor temperature was 6°C/-7°C; the supply water temperature of minor side of heat exchange station in the community was 40°C, the return water temperature of minor side of higher/lower zone was 37°C/36.1°C and the operating frequency of circulating pump in higher/lower zone was 36 Hz/39 Hz. Further, the heat preservation of the minor network had not been finished.

Valve opening and supply and return water temperature at heat inlet of each unit before regulationy.

Heat inlet (lower zone) | Valve opening (%) | Supply/return water temp. (°C) | Heat inlet (higher zone) | Valve opening (%) | Supply/return water temp. (°C) |
---|---|---|---|---|---|

Unit 1 Building 1 | 97 | 35.8/32.6 | Unit 1 Building 1 | 97 | 37.2/31.2 |

Unit 2 Building 1 | 97 | 35.5/31.5 | Unit 2 Building 1 | 97 | 35.2/33.6 |

Unit 3 Building 1 | 97 | 35.5/33.7 | Unit 3 Building 1 | 97 | 37.6/35.6 |

Unit 1 Building 2 | 62 | 37.2/34.4 | Unit 1 Building 2 | 65 | 36.8/34.6 |

Unit 2 Building 2 | 57 | 36.2/34.4 | Unit 2 Building 2 | 97 | 37.4/34.8 |

Unit 1 Building 3 | 13 | 37.4/35.3 | Unit 1 Building 3 | 31 | 37.1/34.7 |

Unit 2 Building 3 | 32 | 37.5/35.1 | Unit 2 Building 3 | 31 | 37.4/34.1 |

Unit 1 Building 4 | 22 | 37.6/35.5 | Unit 1 Building 4 | 27 | 36.4/34.8 |

Unit 2 Building 4 | 22 | 37.6/36.1 | Unit 2 Building 4 | 20 | 36.4/34.2 |

Unit 1 Building 5 | 34 | 38.8/36.1 | Unit 1 Building 6 | 52 | 37.1/35.5 |

Unit 2 Building 5 | 55 | 38.5/34.7 | Unit 2 Building 6 | 47 | 37.1/34.6 |

Unit 1 Building 6 | 43 | 39.1/36.3 | Unit 1 Building 7 | 60 | 37.2/35.3 |

Unit 2 Building 6 | 37 | 39.1/36.1 | Unit 2 Building 7 | 16 | 37.4/35.2 |

Unit 1 Building 7 | 45 | 38.3/35.7 | Unit 1 Building 9 | 76 | 37.4/34.7 |

Unit 2 Building 7 | 56 | 38.5/34.6 | Unit 2 Building 9 | 60 | 37.9/32.5 |

Unit 1 Building 8 | 22 | 38/32 | |||

Unit 2 Building 8 | 22 | 37.3/33.5 | |||

Unit 1 Building 9 | 32 | 38.2/31.8 | |||

Unit 2 Building 9 | 55 | 38.4/35.5 |

From Table 3, it is observed that the valve opening of the heat inlet at each unit is very different and the supply and return water temperatures are varied between 1.8°C and 6.4°C. It indicates that hot water flow into each unit differs greatly and the hydraulic disorder is severe, resulting in uneven indoor temperatures between heat consumers of different units. The heat preservation work of the minor network was completed within the same week. The measured supply water temperature of the network in the tail end of building 1 was the same as the measured supply water temperature of the minor side. The same time period with similar weather data was selected for running the levelling system. On 4 January 2021, the regulation was performed. On that day, the supply water temperature of the minor side was 40°C and in-station operating parameters were stable. See pre-regulation and post-regulation data in Figure 10.

After debugging, the return water temperatures at each heat inlet tend to agree and are controlled between 35°C and 36°C. This indicates that the hot water flow of each unit in the community matches with the heat load, that the uneven temperature difference of each unit in the initial state has been regulated to the maximum extent and that good heat and hydraulic equilibrium are achieved. Besides, in the current working condition, the supply and return water temperature difference of heat consumers in each unit is about 0.013 Mpa. The current valve position is shown in Table 4. All of the monitored indoor temperatures of typical heat consumers in the community are higher than the heating standard and no complaint about super-cold is received from any heat consumer.

Post-regulation valve opening and return water temperature at heat inlet of each unit.

Heat inlet (lower zone) | Valve opening (%) | Return water temp.(°C) | Heat inlet (higher zone) | Valve opening (%) | Return water temp.(°C) |
---|---|---|---|---|---|

Unit 1 Building 1 | 62 | 35.81 | Unit 1 Building 1 | 95 | 35.82 |

Unit 2 Building 1 | 56 | 36.14 | Unit 2 Building 1 | 86 | 35.36 |

Unit 3 Building 1 | 54 | 35.74 | Unit 3 Building 1 | 89 | 36.26 |

Unit 1 Building 2 | 31 | 35.95 | Unit 1 Building 2 | 24.8 | 35.76 |

Unit 2 Building 2 | 22 | 36.36 | Unit 2 Building 2 | 24 | 35.65 |

Unit 1 Building 3 | 20.6 | 35.55 | Unit 1 Building 3 | 26 | 35.67 |

Unit 2 Building 3 | 24 | 35.85 | Unit 2 Building 3 | 28 | 35.66 |

Unit 1 Building 4 | 12.6 | 36.12 | Unit 1 Building 4 | 20.8 | 36 |

Unit 2 Building 4 | 18 | 35.62 | Unit 2 Building 4 | 19 | 35.51 |

Unit 1 Building 5 | 24.8 | 35.73 | Unit 1 Building 6 | 24 | 35.92 |

Unit 2 Building 5 | 26 | 35.84 | Unit 2 Building 6 | 18 | 35.44 |

Unit 1 Building 6 | 14 | 36 | Unit 1 Building 7 | 22 | 35.75 |

Unit 2 Building 6 | 14 | 36.56 | Unit 2 Building 7 | 22 | 35.6 |

Unit 1 Building 7 | 28 | 36.1 | Unit 1 Building 9 | 12 | 36.1 |

Unit 2 Building 7 | 38 | 35.86 | Unit 2 Building 9 | 16 | 36.22 |

Unit 1 Building 8 | 33 | 35.56 | |||

Unit 2 Building 8 | 22 | 35.82 | |||

Unit 1 Building 9 | 16 | 35.78 | |||

Unit 2 Building 9 | 26 | 35.59 |

For each unit controller, the controlled object is the branch pipeline flowing into each heat consumer. The building itself has heat-retaining property, and the temperature adjustment between branches is a process with large capacity delay and pure delay. Through changing valve opening during stable operation of heat exchange station, the step response of controlled objects is studied. When the supply water temperature is 41°C, the valve opening is turned down from 85% to 15%. Correspondingly, when the supply water temperature is 40°C, the valve opening is turned up from 15% to 85%. The data of return water temperature changes with time is recorded, and the step response curve of return water temperature in the process of turning up and down valve is drawn. The generated curves are shown in Figure 11.

In Figure 11, during valve adjustment, if the return water temperature change is delayed for about 30 min, it becomes stable. It is feasible to use first-order inertia elements to substitute into the primary and minor controlled processes and compare it to the single-loop control system. Taking the same damping coefficient, the working frequency ratio can be obtained from Eq. (2):
_{01} and _{02} are the time constants of the primary and minor controlled processes.

It is known from equation analysis that _{primary}/_{minor} increases with _{01}/_{02}. It can be observed from the literature [19, 20] that when _{primary}/_{minor} > 3, the system resonance can be eliminated; then, we can carry out a comprehensive consideration of the dynamic relationship between primary and minor channels of network system and determine the ratio of _{01}/_{02} within a range of ∼3–10, according to the step response curve of controlled object [21, 22]. _{02} is affected by the valve regulating process, stage and time, and is allowed to fluctuate in a smaller scope. Eventually, the sampling cycles of primary and minor loops are determined:

During the network branch regulation, it is required that the return water temperature parameters of unit branches should inter-coordinate to meet systemic dynamic hydraulic equilibrium. The return water temperatures of each branch are allowed to fluctuate in a smaller range and change slowly in balance. The opening of electric regulating valves in each branch of the network system is optimised dynamically, while the measured supply and return water temperatures as minor parameters also fluctuate in a smaller range according to the practical working condition of the heating network. To sum up, the primary regulator shall adopt PI regulation and the minor regulator shall adopt P regulation. Observing Eq. (5), the ratio of the sampling cycles of primary and minor loops is rather big; so, the two-step setting method is used to perform parameter setting of primary and minor regulators. In automatic working conditions, a further setting can be made in the SCADA system interface under the averaging idea. In the following, various parameters of the unit control system at the near-end, middle-section and tail end of the building are used for explanation. Detailed controller parameters are shown in Table 5.

Controller parameters.

Unit No. | Controller | Parameters |
---|---|---|

Higher zone, Unit 2, Building 1 | Primary loop | δ=19.2,I=22.65 min |

Minor loop | δ=29 | |

Lower zone, Unit 1, Building 6 | Primary loop | δ=19.8,I=21.64 min |

Minor loop | δ=29.8 | |

Lower zone, Unit 2, Building 9 | Primary loop | δ=20.4,I=19.8 min |

Minor loop | δ=30.1 |

Comparing the cascade control system of this system to the single-loop return water temperature control system [23], we observe the effect of controlling the same controlled object by network unit branch. In view of that, the optimised unit inlet device can monitor and run these two control systems, and some experiments has been conducted on the above-mentioned three typical units. We obtain the unit return water temperature response curve under the effect of the unit return water temperature – branch pressure difference cascade (averaging) and the single-loop negative-feedback return water temperature regulation system, as shown in Figure 12.

In the same working condition, when the control centre issues the set value _{0} of return water temperature, the control effect of cascade (averaging) controller and single-loop PID controller on network unit branch is analysed. See detailed comparison results of dynamic performance indexes in Table 6.

Comparison of performance indexes of control system.

Working condition | Unit No. | _{r} |
(sing time)/s | δ.(ershoot)/% | t.(mp.fluctuation range)°C |

gh the return water temperature response curve of typical units, an analysis is made on the control performance indexes of network unit branch of the same controlled object by the return water temperature-branch pressure difference cascade (averaging) and the single-loop negative-feedback return water temperature regulation system in the same working condition in Table the proposed return water temperature-branch pressure difference cascade control system, relative control parameters are further regulated using the averaging control idea. Though there is a long rising time in the response curve of lower zone, unit 2, building 9, by observing the curves in Figure 8, certain dynamic disturbance exists in return water temperatures of each unit branch. This is detrimental to the stability of the minor network system and the service life of valves. By observing the response curve designed in this system, the influence of disturbance can be eliminated and the self-adaptive capability of the network system can be enhanced. Through comprehensive analysis, it is identified that compared to singleloop PID controller, the cascade (averaging) controller has a better control effect, smaller overshoot, stronger anti-disturbance capability and good dynamic behaviour. So it can quickly respond to disturbance factors in the minor network system, keep the return water temperature in a smaller range, promote network equilibrium and stability and satisfy the practical systemic need of static and dynamic hydraulic equilibrium.

Through optimising unit inlet device and applying new control theory, this system establishes a levelling system of minor heating network and designs a cascade control system of return water temperature _{H}_{L}^{2} and heating area of 43,188.62 m^{2}, it greatly improves the non-equilibrium of indoor temperature at the heat consumer side. When the self-designed SCADA system is used to monitor the on-site application effect, the return water temperature response time curve of each unit branch and various performance indexes are obtained. The results show that compared to traditional singleloop negative-feedback return water temperature control system, the cascade (averaging) controller has a better control effect, smaller overshoot and stronger anti-disturbance capacity than single-loop PID controller, which adapts to the minor network system with large time delay and inertia dynamic characteristic. Cascade controller is able to quickly cope with systemic disturbance factors and enables return water temperature between units to inter-coordinate and thus be maintained within a smaller range. It effectively eliminates the influence of static and dynamic hydraulic disorder on entire system stability, and plays a good role in project demonstration and guiding.

#### Statistics of building condition in the community.

SN | Building No. | Unit qty. | Floor qty. | Construction area (m^{2}) |
Heating supply area (m^{2}) |
---|---|---|---|---|---|

1 | #1 | 3 | 18 | 23086.5 | 7632.46 |

2 | #2 | 2 | 18 | 9781 | 2337.86 |

3 | #3 | 2 | 18 | 15309.36 | 5181.87 |

4 | #4 | 2 | 18 | 16465.4 | 4188.8 |

5 | #5 | 2 | 12 | 10113.6 | 4194.52 |

6 | #6 | 2 | 18 | 16465.4 | 7502.58 |

7 | #7 | 2 | 18 | 9558.21 | 4501.11 |

8 | #8 | 2 | 11 | 9279.6 | 4254.63 |

9 | #9 | 2 | 16 | 8431.84 | 3394.79 |

#### Comparison of performance indexes of control system.

Working condition | Unit No. | _{r} |
(sing time)/s | δ.(ershoot)/% | t.(mp.fluctuation range)°C |

#### Valve opening and supply and return water temperature at heat inlet of each unit before regulationy.

Heat inlet (lower zone) | Valve opening (%) | Supply/return water temp. (°C) | Heat inlet (higher zone) | Valve opening (%) | Supply/return water temp. (°C) |
---|---|---|---|---|---|

Unit 1 Building 1 | 97 | 35.8/32.6 | Unit 1 Building 1 | 97 | 37.2/31.2 |

Unit 2 Building 1 | 97 | 35.5/31.5 | Unit 2 Building 1 | 97 | 35.2/33.6 |

Unit 3 Building 1 | 97 | 35.5/33.7 | Unit 3 Building 1 | 97 | 37.6/35.6 |

Unit 1 Building 2 | 62 | 37.2/34.4 | Unit 1 Building 2 | 65 | 36.8/34.6 |

Unit 2 Building 2 | 57 | 36.2/34.4 | Unit 2 Building 2 | 97 | 37.4/34.8 |

Unit 1 Building 3 | 13 | 37.4/35.3 | Unit 1 Building 3 | 31 | 37.1/34.7 |

Unit 2 Building 3 | 32 | 37.5/35.1 | Unit 2 Building 3 | 31 | 37.4/34.1 |

Unit 1 Building 4 | 22 | 37.6/35.5 | Unit 1 Building 4 | 27 | 36.4/34.8 |

Unit 2 Building 4 | 22 | 37.6/36.1 | Unit 2 Building 4 | 20 | 36.4/34.2 |

Unit 1 Building 5 | 34 | 38.8/36.1 | Unit 1 Building 6 | 52 | 37.1/35.5 |

Unit 2 Building 5 | 55 | 38.5/34.7 | Unit 2 Building 6 | 47 | 37.1/34.6 |

Unit 1 Building 6 | 43 | 39.1/36.3 | Unit 1 Building 7 | 60 | 37.2/35.3 |

Unit 2 Building 6 | 37 | 39.1/36.1 | Unit 2 Building 7 | 16 | 37.4/35.2 |

Unit 1 Building 7 | 45 | 38.3/35.7 | Unit 1 Building 9 | 76 | 37.4/34.7 |

Unit 2 Building 7 | 56 | 38.5/34.6 | Unit 2 Building 9 | 60 | 37.9/32.5 |

Unit 1 Building 8 | 22 | 38/32 | |||

Unit 2 Building 8 | 22 | 37.3/33.5 | |||

Unit 1 Building 9 | 32 | 38.2/31.8 | |||

Unit 2 Building 9 | 55 | 38.4/35.5 |

#### Controller parameters.

Unit No. | Controller | Parameters |
---|---|---|

Higher zone, Unit 2, Building 1 | Primary loop | δ=19.2,I=22.65 min |

Minor loop | δ=29 | |

Lower zone, Unit 1, Building 6 | Primary loop | δ=19.8,I=21.64 min |

Minor loop | δ=29.8 | |

Lower zone, Unit 2, Building 9 | Primary loop | δ=20.4,I=19.8 min |

Minor loop | δ=30.1 |

#### Post-regulation valve opening and return water temperature at heat inlet of each unit.

Heat inlet (lower zone) | Valve opening (%) | Return water temp.(°C) | Heat inlet (higher zone) | Valve opening (%) | Return water temp.(°C) |
---|---|---|---|---|---|

Unit 1 Building 1 | 62 | 35.81 | Unit 1 Building 1 | 95 | 35.82 |

Unit 2 Building 1 | 56 | 36.14 | Unit 2 Building 1 | 86 | 35.36 |

Unit 3 Building 1 | 54 | 35.74 | Unit 3 Building 1 | 89 | 36.26 |

Unit 1 Building 2 | 31 | 35.95 | Unit 1 Building 2 | 24.8 | 35.76 |

Unit 2 Building 2 | 22 | 36.36 | Unit 2 Building 2 | 24 | 35.65 |

Unit 1 Building 3 | 20.6 | 35.55 | Unit 1 Building 3 | 26 | 35.67 |

Unit 2 Building 3 | 24 | 35.85 | Unit 2 Building 3 | 28 | 35.66 |

Unit 1 Building 4 | 12.6 | 36.12 | Unit 1 Building 4 | 20.8 | 36 |

Unit 2 Building 4 | 18 | 35.62 | Unit 2 Building 4 | 19 | 35.51 |

Unit 1 Building 5 | 24.8 | 35.73 | Unit 1 Building 6 | 24 | 35.92 |

Unit 2 Building 5 | 26 | 35.84 | Unit 2 Building 6 | 18 | 35.44 |

Unit 1 Building 6 | 14 | 36 | Unit 1 Building 7 | 22 | 35.75 |

Unit 2 Building 6 | 14 | 36.56 | Unit 2 Building 7 | 22 | 35.6 |

Unit 1 Building 7 | 28 | 36.1 | Unit 1 Building 9 | 12 | 36.1 |

Unit 2 Building 7 | 38 | 35.86 | Unit 2 Building 9 | 16 | 36.22 |

Unit 1 Building 8 | 33 | 35.56 | |||

Unit 2 Building 8 | 22 | 35.82 | |||

Unit 1 Building 9 | 16 | 35.78 | |||

Unit 2 Building 9 | 26 | 35.59 |

#### I/O point address assignment.

Input | Output | ||
---|---|---|---|

I0.0 | System On | Q0.0 | Automatic operation indicator |

I0.1 | System Off | Q0.1 | Comprehensive alarm indicator |

I0.2 | Manu/Auto switchover | Q0.2 | Out-of-control valve in unit #1 higher zone |

I0.3 | Emergency cut-off | Q0.3 | Out-of-control valve in unit #1 lower zone |

AIW16 | Return water temperature in unit #1 higher zone | Q0.4 | Out-of-control valve in unit #2 higher zone |

AIW18 | Return water temperature in unit #1 lower zone | Q0.5 | Out-of-control valve in unit #2 lower zone |

AIW20 | Return water temperature in unit #2 higher zone | Q0.6 | Return water temperature alarm in unit #1 |

AIW22 | Return water temperature in unit #2 lower zone | Q0.7 | Return water temperature alarm in unit #2 |

AIW24 | Supply water pressure in unit #1 higher zone | Q1.0 | Supply and return pressure difference alarm in unit #1 |

AIW26 | Return water pressure in unit #1 higher zone | Q1.1 | Supply and return pressure difference alarm in unit #2 |

AIW28 | Supply water pressure in unit #1 lower zone | AQW48 | #1 Higher valve opening instruction |

AIW30 | Return water pressure in unit #1 lower zone | AQW50 | #1 Lower valve opening instruction |

AIW32 | Supply water pressure in unit #2 higher zone | AQW52 | #2 Higher valve opening instruction |

AIW34 | Return water pressure in unit #2 higher zone | AQW54 | #2 Lower valve opening instruction |

AIW36 | Supply water pressure in unit #2 lower zone | ||

AIW38 | Return water pressure in unit #2 lower zone | ||

AIW40 | Valve feedback in unit #1 higher zone | ||

AIW42 | Valve feedback in unit #1 lower zone | ||

AIW44 | Valve feedback in unit #2 higher zone | ||

AIW46 | Valve feedback in unit #2 lower zone |

Law of interest rate changes in financial markets based on the differential equation model of liquidity Basalt fibre continuous reinforcement composite pavement reinforcement design based on finite element model Industrial transfer and regional economy coordination based on multiple regression model Satisfactory consistency judgement and inconsistency adjustment of linguistic judgement matrix Spatial–temporal graph neural network based on node attention A contrastive study on the production of double vowels in Mandarin Research of cascade averaging control in hydraulic equilibrium regulation of heating pipe network Mathematical analysis of civil litigation and empirical research of corporate governance Health monitoring of Bridges based on multifractal theory Health status diagnosis of the bridges based on multi-fractal de-trend fluctuation analysis Performance evaluation of college laboratories based on fusion of decision tree and BP neural network Application and risk assessment of the energy performance contracting model in energy conservation of public buildings Sensitivity analysis of design parameters of envelope enclosure performance in the dry-hot and dry-cold areas Analysis of the relationship between industrial agglomeration and regional economic growth based on the multi-objective optimisation model Constraint effect of enterprise productivity based on constrained form variational computing The impact of urban expansion in Beijing and Metropolitan Area urban heat Island from 1999 to 2019 TOPSIS missile target selection method supported by the posterior probability of target recognition Ultrasonic wave promoting ice melt in ice storage tank based on polynomial fitting calculation model The incentive contract of subject librarians in university library under the non-linear task importance Application of Fuzzy Mathematics Calculation in Quantitative Evaluation of Students’ Performance of Basketball Jump Shot Visual error correction of continuous aerobics action images based on graph difference function Application of Higher Order Ordinary Differential Equation Model in Financial Investment Stock Price Forecast Application of Forced Modulation Function Mathematical Model in the Characteristic Research of Reflective Intensity Fibre Sensors Radioactive source search problem and optimisation model based on meta-heuristic algorithm Research on a method of completeness index based on complex model Fake online review recognition algorithm and optimisation research based on deep learning Research on the sustainable development and renewal of Macao inner harbour under the background of digitisation Support design of main retracement passage in fully mechanised coal mining face based on numerical simulation Study on the crushing mechanism and parameters of the two-flow crusher Interaction design of financial insurance products under the Era of AIoT Modeling the pathway of breast cancer in the Middle East Corporate social responsibility fulfilment, product-market competition and debt risk: Evidence from China ARMA analysis of the green innovation technology of core enterprises under the ecosystem – Time series data Reconstruction of multimodal aesthetic critical discourse analysis framework Image design and interaction technology based on Fourier inverse transform What does students’ experience of e-portfolios suggest Research on China interregional industrial transformation slowdown and influencing factors of industrial transformation based on numerical simulation The medical health venture capital network community structure, information dissemination and the cognitive proximity Data mining of Chain convenience stores location The optimal model of employment and entrepreneurship models in colleges and universities based on probability theory and statistics A generative design method of building layout generated by path Parameter Id of Metal Hi-pressure State Equation Analysis of the causes of the influence of the industrial economy on the social economy based on multiple linear regression equation Research of neural network for weld penetration control P-Matrix Reasoning and Information Intelligent Mining Intelligent Recommendation System for English Vocabulary Learning – Based on Crowdsensing Regarding new wave distributions of the non-linear integro-partial Ito differential and fifth-order integrable equations Research on predictive control of students’ performance in PE classes based on the mathematical model of multiple linear regression equation Beam control method for multi-array antennas based on improved genetic algorithm The influence of X fuzzy mathematical method on basketball tactics scoring Application of regression function model based on panel data in bank resource allocation financial risk management Research on aerobics training posture motion capture based on mathematical similarity matching statistical analysis Application of Sobolev-Volterra projection and finite element numerical analysis of integral differential equations in modern art design Influence of displacement ventilation on the distribution of pollutant concentrations in livestock housing Research on motion capture of dance training pose based on statistical analysis of mathematical similarity matching Application of data mining in basketball statistics Application of B-theory for numerical method of functional differential equations in the analysis of fair value in financial accounting Badminton players’ trajectory under numerical calculation method Research on the influence of fuzzy mathematics simulation model in the development of Wushu market Study on audio-visual family restoration of children with mental disorders based on the mathematical model of fuzzy comprehensive evaluation of differential equation Difference-in-differences test for micro effect of technological finance cooperation pilot in China Application of multi-attribute decision-making methods based on normal random variables in supply chain risk management Exploration on the collaborative relationship between government, industry, and university from the perspective of collaborative innovation The impact of financial repression on manufacturing upgrade based on fractional Fourier transform and probability AtanK-A New SVM Kernel for Classification Validity and reliability analysis of the Chinese version of planned happenstance career inventory based on mathematical statistics Visual positioning system for marine industrial robot assembly based on complex variable function Mechanical behaviour of continuous girder bridge with corrugated steel webs constructed by RW Research on the influencing factors of agricultural product purchase willingness in social e-commerce situation Study of a linear-physical-programming-based approach for web service selection under uncertain service quality A mathematical model of plasmid-carried antibiotic resistance transmission in two types of cells Fractional Differential Equations in the Exploration of Geological and Mineral Construction Burnout of front-line city administrative law-enforcing personnel in new urban development areas: An empirical research in China The Law of Large Numbers in Children's Education Data structure simulation for the reform of the teaching process of university computer courses Calculating university education model based on finite element fractional differential equations and macro-control analysis Educational research on mathematics differential equation to simulate the model of children's mental health prevention and control system Analysis of enterprise management technology and innovation based on multilinear regression model Verifying the validity of the whole person model of mental health education activities in colleges based on differential equation RETRACTION NOTE Innovations to Attribute Reduction of Covering Decision System Based on Conditional Information Entropy Research on the mining of ideological and political knowledge elements in college courses based on the combination of LDA model and Apriori algorithm Adoption of deep learning Markov model combined with copula function in portfolio risk measurement Good congruences on weakly U-abundant semigroups Research on the processing method of multi-source heterogeneous data in the intelligent agriculture cloud platform Mathematical simulation analysis of optimal detection of shot-putters’ best path Internal control index and enterprise growth: An empirical study of Chinese listed-companies in the automobile manufacturing industry Determination of the minimum distance between vibration source and fibre under existing optical vibration signals: a study Nonlinear differential equations based on the B-S-M model in the pricing of derivatives in financial markets Nonlinear Differential Equations in the Teaching Model of Educational Informatisation Fed-UserPro: A user profile construction method based on federated learning Smart Communities to Reduce Earthquake Damage: A Case Study in Xinheyuan, China Response Model of Teachers’ Psychological Education in Colleges and Universities Based on Nonlinear Finite Element Equations Institutional investor company social responsibility report and company performance Mathematical analysis of China's birth rate and research on the urgency of deepening the reform of art education Precision Machining Technology of Jewelry on CNC Machine Tool Based on Mathematical Modeling First-principles calculations of magnetic and mechanical properties of Fe-based nanocrystalline alloy Fe _{80}Si_{10}Nb_{6}B_{2}Cu_{2}Computer Vision Communication Technology in Mathematical Modeling The Effect of Children’s Innovative Education Courses Based on Fractional Differential Equations Fractional Differential Equations in the Standard Construction Model of the Educational Application of the Internet of Things Optimization in Mathematics Modeling and Processing of New Type Silicate Glass Ceramics Has the belt and road initiative boosted the resident consumption in cities along the domestic route? – evidence from credit card consumption MCM of Student’s Physical Health Based on Mathematical Cone Attitude control for the rigid spacecraft with the improved extended state observer Sports health quantification method and system implementation based on multiple thermal physiology simulation Research on visual optimization design of machine–machine interface for mechanical industrial equipment based on nonlinear partial equations Research on identifying psychological health problems of college students by logistic regression model based on data mining Abnormal Behavior of Fractional Differential Equations in Processing Computer Big Data Mathematical Modeling Thoughts and Methods Based on Fractional Differential Equations in Teaching A mathematical model of PCNN for image fusion with non-sampled contourlet transform Nonlinear Differential Equations in Computer-Aided Modeling of Big Data Technology The Uniqueness of Solutions of Fractional Differential Equations in University Mathematics Teaching Based on the Principle of Compression Mapping Influence of displacement ventilation on the distribution of pollutant concentrations in livestock housing Cognitive Computational Model Using Machine Learning Algorithm in Artificial Intelligence Environment Application of Higher-Order Ordinary Differential Equation Model in Financial Investment Stock Price Forecast Recognition of Electrical Control System of Flexible Manipulator Based on Transfer Function Estimation Method Automatic Knowledge Integration Method of English Translation Corpus Based on Kmeans Algorithm Real Estate Economic Development Based on Logarithmic Growth Function Model Informatisation of educational reform based on fractional differential equations Financial Crisis Early Warning Model of Listed Companies Based on Fisher Linear Discriminant Analysis Research on the control of quantitative economic management variables under the numerical method based on stochastic ordinary differential equations Network monitoring and processing accuracy of big data acquisition based on mathematical model of fractional differential equation 3D Animation Simulation of Computer Fractal and Fractal Technology Combined with Diamond-Square Algorithm The Summation of Series Based on the Laplace Transformation Method in Mathematics Teaching Optimal Solution of the Fractional Differential Equation to Solve the Bending Performance Test of Corroded Reinforced Concrete Beams under Prestressed Fatigue Load Radial Basis Function Neural Network in Vibration Control of Civil Engineering Structure Optimal Model Combination of Cross-border E-commerce Platform Operation Based on Fractional Differential Equations Research on Stability of Time-delay Force Feedback Teleoperation System Based on Scattering Matrix BIM Building HVAC Energy Saving Technology Based on Fractional Differential Equation Human Resource Management Model of Large Companies Based on Mathematical Statistics Equations Data Forecasting of Air-Conditioning Load in Large Shopping Malls Based on Multiple Nonlinear Regression System dynamics model of output of ball mill Optimisation of Modelling of Finite Element Differential Equations with Modern Art Design Theory Mathematical function data model analysis and synthesis system based on short-term human movement Sensitivity Analysis of the Waterproof Performance of Elastic Rubber Gasket in Shield Tunnel Human gait modelling and tracking based on motion functionalisation Analysis and synthesis of function data of human movement The Control Relationship Between the Enterprise's Electrical Equipment and Mechanical Equipment Based on Graph Theory Financial Accounting Measurement Model Based on Numerical Analysis of Rigid Normal Differential Equation and Rigid Functional Equation Mathematical Modeling and Forecasting of Economic Variables Based on Linear Regression Statistics Design of Morlet wavelet neural network to solve the non-linear influenza disease system Nonlinear Differential Equations in Cross-border E-commerce Controlling Return Rate Differential equation model of financial market stability based on Internet big data 3D Mathematical Modeling Technology in Visualized Aerobics Dance Rehearsal System Children’s cognitive function and mental health based on finite element nonlinear mathematical model Motion about equilibrium points in the Jupiter-Europa system with oblateness Fractional Differential Equations in Electronic Information Models Badminton players’ trajectory under numerical calculation method BIM Engineering Management Oriented to Curve Equation Model Optimal preview repetitive control for impulse-free continuous-time descriptor systems Development of main functional modules for MVB and its application in rail transit Study on the impact of forest fire prevention policy on the health of forest resources Mathematical Method to Construct the Linear Programming of Football Training The Size of Children's Strollers of Different Ages Based on Ergonomic Mathematics Design Stiffness Calculation of Gear Hydraulic System Based on the Modeling of Nonlinear Dynamics Differential Equations in the Progressive Method Relationship Between Enterprise Talent Management and Performance Based on the Structural Equation Model Method Value Creation of Real Estate Company Spin-off Property Service Company Listing Selection by differential mortality rates Digital model creation and image meticulous processing based on variational partial differential equation Dichotomy model based on the finite element differential equation in the educational informatisation teaching reform model Nonlinear Dissipative System Mathematical Equations in the Multi-regression Model of Information-based Teaching The modelling and implementation of the virtual 3D animation scene based on the geometric centre-of-mass algorithm The policy efficiency evaluation of the Beijing–Tianjin–Hebei regional government guidance fund based on the entropy method The transfer of stylised artistic images in eye movement experiments based on fuzzy differential equations Research on behavioural differences in the processing of tenant listing information: An eye-movement experiment A review of the treatment techniques of VOC Some classes of complete permutation polynomials in the form of ( x ^{pm}−x +δ )^{s}+ax ^{pm}+bx overF _{p2m}The consistency method of linguistic information and other four preference information in group decision-making Research on the willingness of Forest Land’s Management Rights transfer under the Beijing Forestry Development A mathematical model of the fractional differential method for structural design dynamics simulation of lower limb force movement step structure based on Sanda movement Fractal structure of magnetic island in tokamak plasma Numerical calculation and study of differential equations of muscle movement velocity based on martial articulation body ligament tension Study on the maximum value of flight distance based on the fractional differential equation for calculating the best path of shot put Sports intensity and energy consumption based on fractional linear regression equation Analysis of the properties of matrix rank and the relationship between matrix rank and matrix operations Study on Establishment and Improvement Strategy of Aviation Equipment Research on Financial Risk Early Warning of Listed Companies Based on Stochastic Effect Mode Characteristics of Mathematical Statistics Model of Student Emotion in College Physical Education Mathematical Calculus Modeling in Improving the Teaching Performance of Shot Put Application of Nonlinear Differential Equation in Electric Automation Control System Nonlinear strategic human resource management based on organisational mathematical model Higher Mathematics Teaching Curriculum Model Based on Lagrangian Mathematical Model Optimization of Color Matching Technology in Cultural Industry by Fractional Differential Equations The Marketing of Cross-border E-commerce Enterprises in Foreign Trade Based on the Statistics of Mathematical Probability Theory The Evolution Model of Regional Tourism Economic Development Difference Based on Spatial Variation Function The Inner Relationship between Students' Psychological Factors and Physical Exercise Based on Structural Equation Model (SEM) Fractional Differential Equations in Sports Training in Universities Higher Education Agglomeration Promoting Innovation and Entrepreneurship Based on Spatial Dubin Model